KSPC - PHUC MINH CO.,LTD

http://www.kspc.com.vn

KSFLD TYPE FLAME ARRESTER

The model KSFL inline detonation flame arrester is designed, manufactured and tested according to API 2000, British Standard Specification Code BS7244, and EN 12874 / ISO 16852.
The units are passive devices with no moving parts.
The KSFL detonation flame arresters provide protection against flame propagation in piping systems that are manifolded or have long runs. The arresters are designed to stop an ignited flammable vapor mixture traveling at subsonic or supersonic vapor velocities.
They are also designed to protect against continuous burning against the 316LSS flame cell for a specific period.
 

The standard flame cell is suitable for NEC group D or IEC IIA gases. Cells for other gas groups are available as additional extras.
The standard design shall be used up to an operating temperature of + 60 deg C / 140 deg F and operating pressure up to 1.1 bar abs from size ½” / 15A to 12” / DN 300. Upon request, it can be obtained for higher pressure and higher temperature with special approval.
The flame arresters are available with either carbon steel (epoxy coated), 304SS, or 316SS housing with 316LSS flame cells.
Sizes range from 25mm to 600mm.
Standard flanges are ANSI 150lb and other connections are available upon request.


MAINTENANCE

Periodic inspection and maintenance is required. The cell assembly can be removed for cleaning purposes. Cleaning ban be accomplished by dipping the entire cell assembly into an appropriate solvent. Care should be taken not to damage the cell openings as such deformations hamper the flow through the cell. The gaskets should be inspected and replaced if necessary.

KSFLD TYPE FLAME ARRESTER

 KSFLD 설치.

You did not use the site, Click here to remain logged. Timeout: 60 second